For cooling tower products and applications, the industry defines the effectiveness of a drift eliminator product in terms of its drift rate. This rating is usually presented in the form of a percentage. You may ask, “Percentage of what?”… Percentage of circulating water flow rate!
Let’s use this tower design criteria as an example so that we can work through the calculation together:
Entering Water Temp: 95°F
Exiting Water Temp: 85°F
Site Wetbulb Temp: 78°F
Circulating Flow Rate: 1,000 gpm
If this is a counterflow cooling tower where we plan to utilize the CF80MAx drift eliminator, we can look at the published drift rate for this product and see it is 0.0005%. Since we now know that this percentage is in relation to the circulating flow rate, we can calculate the volume of water exiting out of the tower in the form of drift droplets, or “drift loss,” as such:
Drift Loss (gal/m) = 1000 gal/min x (0.0005/100) = 0.005 gal/min
Expressed over an hour period: 0.005 gal/min x 60 min/hr = 0.3 gal/hr
If we substitute another product’s drift rating of 0.002%, we would get a drift loss of 1.2 gal/hr, or 4 TIMES GREATER drift loss.
Hopefully this provides a clear example and/or refresher on a drift eliminator’s drift rate. The next question is, “Where does a manufacturer get that drift rate number, and is that rate consistent as my fan rpm changes?” We’ll tackle that topic in a separate article!
Brentwood was introduced to the transportation industry in 1971 by its parent company at the time, the Dana Corporation. Dana had been making drivetrain parts for heavy-duty trucks and realized that Brentwood’s thermoforming capabilities could be used to expand the…Read More
In today’s stormwater market, there are two main product types used to manage runoff in subsurface applications: box systems and arch-shaped products. Both are designed to accomplish the same function: create a void space for stormwater and support the surface…Read More
Brentwood knows that there’s more to your cooling tower than the fill and drift eliminators we supply. In fact, the primary maintenance task for cooling towers revolves around water treatment. Unfortunately, there is no “one size fits all” water treatment…Read More